-- eight generating units are retrofitted with hgm9510 to realize parallel connection of different powers
The site condition of this case is that there are four 500 kW Cummins generators and four 800 kW Cummins units, two generator rooms, one is four 500 kW units, the other is four 800 kW units. The original two groups of generating units are in parallel, and the parallel effect of the old system is poor, and the parallel failure and uneven load distribution often occur.
By using hgm9510 in parallel, the two can be combined into one.The MSc communication distance between the 8 units is 50 meters. The MSc communication of the first unit and the MSc communication of the last unit need a 120 Ω matching resistor in parallel.Users can easily realize the parallel connection of 8 units through "3 keys" (manual key, start key and closing key).The operation is simple and the performance is reliable.So that users no longer have to worry about parallel failure and uneven load distribution.
Application diagram of multi machine parallel connection
Xiaobian believes that with the rapid development of science and technology and the popularization of AI intelligence, the future will be more simple and beautiful. Come on smartgen and China.